I have a 3-phase blower motor that I am looking to control from a Danfoss VLT 2800 that I purchased on eBay.
I have in the shop a receptacle that looks like this:
If I put a meter from neutral (horizontal middle) to either hot side (the verticals) I get 120v. Across the hots I get 240v. The table suggests that for single phase I should only be connecting two wires, including a neutral. But with the neutral I have I only get the 120v. Should I just be connecting the two hots?
For reference, our building has high-leg delta service.