# Is a current limiter recommended for an isolation transformer rig?

Something I've been meaning to do for a while, but never quite got around to, is to build an isolation transformer unit. So, I was pretty happy when I got my hands on a couple of identical 240V to 24V 96VA step down transformers in good condition.

They look well made and are pretty heavy with a 1 Amp slow blow fuse on the primary and a 5 Amp slow blow on the secondary. So, they've allowed for a slightly higher output current than the rating otherwise indicates. There is one primary winding (240V) and one secondary winding (24V loaded).

My plan is to connect the secondary windings together (so 240V in and 220V-ish out) with a 1 Amp slow blow on the load side. However, whilst the current draw is fine for most light project work, inevitably you'll attach a poorly understood load and end up blowing fuses all the time. I won't include a diagram on this occasion, since the setup I described is trivial.

So, my question is simple, is it recommended to install a current limiting circuit (or component) to limit the output current to below 1 Amp or is this overkill?

UPDATE: Andy asked that I measure the magnetizing current into the transformer pair and, as much as I like a good old spark-off, the results are quite interesting (to me anyway!).

I left one of primary windings open circuit, then I soldered the two secondaries together. I connected the other primary winding in series (hot side) with a 100W 1 Ohm resistor. The DMM is a trusted true RMS model and I measured the resistor with a very accurate LCR meter, which turned out to be 1.04 ohms.

Powering up the circuit and applying 240V mains I read 0.146V AC(rms) across the resistor. If I'm not mistaken that's over 200mA peak magnetizing current draw, which I must say I found pretty amazing. Anyway, there you go.

• "inevitably you'll attach an poorly understood load and end up blowing fuses all the time. " -- Isn't this what fuses are for?? – Scott Seidman Dec 7 '16 at 14:47
• That's true and I normally pay attention to these things. I'm just curious as to whether this is ever really done and if not, why not. – Buck8pe Dec 7 '16 at 14:50
• It seems unlikely to me that you will get 240 V out but probably something a bit less like 230 V or 220 V. – Andy aka Dec 7 '16 at 14:50
• Yep. Understood. I've read that as part of my research and it's OK for what I need. – Buck8pe Dec 7 '16 at 14:51
• So use a resettable fuse? – PlasmaHH Dec 7 '16 at 15:24

with a 1 Amp slow blow fuse on the primary

Given that your secondary fuse rating implies a load of 120 VA and your primary fuse rating implies an input of 240 VA it could be argued that the magnetization current into the primary is in the order of 0.5 amps$^1$ leaving 0.5 amps for real load current seen at the primary (0.5 amps x 240 volts = 120 VA).

This implies to me that your output fuse should be significantly smaller than 1 amp i.e. more like 0.5 amps because if you were to take 1 amp from the output winding of the dual-connected transformer, you would inevitably be taking 1.5 amps into the primary of the transformer connected to raw mains and this could cause a fire.

is it recommended to install a current limiting circuit (or component) to limit the output current to below 1 Amp or is this overkill?

Given the info you have provided I have to be cautious and say that the output fuse should be no more than 0.5 amps. You will still need to use a 1 A input fuse too.....

But, there is a further consideration. The transformer that is receiving the main AC input is not only taking magnetization current for its own core but supplying magnetization current for the other transformer's core.

It logically follows that in the dual connected scenario, the 1st transformer might be taking up to 1 amp just to magnetize both cores leaving you with no headroom for load current.

There is insufficient information to safely conclude anything else so, I would recommend you measure the primary current (nothing on the secondary) and, if you find it to be (say) 0.25 amps you can also assume that it will be 0.5 amps when both transformers are cascaded. This would mean that your output fuse should be 0.5 amps.

$^1$ This is a bit of an approximation and underlies the basic problem of cascading transformers. If the full rated primary current is 1 amp and this current contains 0.5 amps of contribution from a 120 VA load, magnetization current could be as high as $\sqrt{1^2 - 0.5^2}$ = 0.866 amps RMS. The square root calculation takes into account that magnetization current is due to primary inductance and this will normally be 90 degrees shifted to resistive load current. However with two cascaded transformers the total magnetization current could, theoretically be as high as 2 x 0.866 amps. It's very problematic cascading transformers like this.

• Food for thought indeed! I hadn't realized the magnetization current could be so large. I may need to hold out for a bigger transformer. One thing I'm not completely clear on...why the 1 Amp fuse at the input? Wouldn't the 1/2 Amp fuse on the secondary be enough? – Buck8pe Dec 7 '16 at 16:03
• The original transforer had a 1 A fuse at the input so it's a fair bet that it's safe to use one now. Please let me know what current you measure when the secondary is unconnected. – Andy aka Dec 7 '16 at 20:35
• I measured that magnetizing current at about 200mA peak (see question update). Not quite as high as you were saying, but higher than I was expecting so I appreciate the comments and (more importantly), I've learned something new. – Buck8pe Dec 7 '16 at 20:51
• @Buck8pe great, that looks fine then but, you understand that being cautious is important when connecting stuff to the power sockets. You should be able to get nearly full load output VA (reduced output voltage). – Andy aka Dec 7 '16 at 21:03
• @Buck8pe. You measured the magnetizing current for both transformers since you connected the secondary's together. So you might expect that a single transformer has about 100 mA magnetizing current, which sounds much more reasonable than 866 mA. – Jack Creasey Dec 7 '16 at 23:40

You only require a single Fuse on the input to your identical cascaded transformers. The only potential to get in trouble is if you use a lower VA rating for the second transformer. You are at all times limited by the VA rating of the first transformer, and if it's Slow-blow input fuse is correctly rated to protect it, then the transformer pair is adequately protected (provide the second transformer is of an equal or lower VA rating).

You have: 240 V --> 24 V --> 24 V --> 240 V

No matter the load you have on the final transformer, all the power is supplied from the first one, it is therefore impossible to overload the second if it has the same rating as the first. You could for example connect a 100 VA first transformer to a 500 VA second transformer. You can never exceed the 100 VA rating of the first transformers input protection fuse capability, and apart from asymmetrical losses in the two transformers nothing can go wrong. .

No matter what the input voltage is (220-230-240) you will get very close to that voltage output providing the turns ratio of the transformers is the same. No matter what it is, the combined turns ratio is fixed.
The transformer output voltage will droop more with load than a single transformer would, but providing you keep below the total VA rating of the first transformer it should be tolerable for your task (isolation).

The transformer losses add. So you have to consider:
1. Eddy-current losses
2. I^R losses for all windings