# How can i make my 380/380 volts motor to run on 220 volts?

I bought a small and old combi woodworking machine "Emco Start". The Machine is running 380v. The problem is that i only have 220 at home. I made some research and i found out that it is possible to get it run on 220 volts, by adding a Capacitor. My problem is that i am not not how to wire it to the motor, and i am not sure what is the needed value of the capacitor ( It has a switch, so it runs with two speeds)

The label on the motor shows : Volts : 380/380 KW : 0,37/0,51 U/min : 1430/2860

the wiring taken from the schematics is attached here. Thanks

U, V, U => from the motor to the switch (speed 1) WV, MV, VU => from the motor to the switch (speed 2)

• That's a three phase motor. How many 220V phases do you have at home? – Jack B Jan 13 '17 at 13:08
• "380 kW" and "small" are contradictory IMHO. Resolve the anomaly then buy a 220 V motor if you value your time. – Andy aka Jan 13 '17 at 13:11
• Look for "Variable Frequency Drive" with a competent supplier. Some (but not all) may be able to do what you need - providing 3 phase from single phase input. Note - some may only provide 3 phase 208V so don't just assume any VFD will work. – Brian Drummond Jan 13 '17 at 13:18
• @Andy : that's "Volts : 380" and "Kw: 0.37" so pretty small. – Brian Drummond Jan 13 '17 at 13:19
• @BrianDrummond I'll take your word for it LOL – Andy aka Jan 13 '17 at 13:26

The connection of a capacitor to a three-phase motor for single-phase operation is called a Steinmetz connection. If you search "Steinmetz connection" you will quite a bit of information about that.

If the motor has only six leads or terminals available for external connections, it can only be operated at 380 volts at either of the two speeds indicated. For low speed, U4, V4 and W4 are connected together and three-phase power is connected to U2, V2 and W2. For high-speed operation, there is no connection to U2, T2 and W2, and power is connected to Uw, T4 and W4. The mechanical power rating is the same for both speeds, so the torque available at the high speed is half of the low speed torque. You could use a variable frequency drive (VFD) with 380 volt output for either of those connections.

If each end of each winding is available independent external connection, 12-leads or terminals, the windings could possibly be connected in a parallel delta configuration. That should be suitable for 220 volt, 3-phase power. I believe that would still be the 4-pole, low-speed configuration. You could use a VFD with 220 volt output for that connection.

You should have no problem finding a VFD with 220 volt, single phase input and 220 volt, three-phase output. You might be able to find a VFD with a built-in voltage boost circuit to give 380 volt, three-phase output with 220 volt, single-phase input. Otherwise you would need an input transformer for the VFD and a 380 volt VFD that accepts single-phase input.

I don't know what all the options are with a Steinmetz connection.

Unless the existing motor has a special shaft or a gear mounted directly to it. The best option may be to buy a different motor and perhaps a VFD for speed control.

See diagram below:

For U2, V2 and W2, two motor coils are connected together inside the motor or in the motor terminal box. If you can break that connection, you can reconnect the coils as shown by the red lines. I am pretty sure that will allow the motor to run at the high speed on 220 volts. For single phase, connect a capacitor from one of the power lines to the point where the missing phase would be connected. That allows the motor to run on single-phase, but the torque capability is greatly reduced. This is the Steinmetz connection. You should be able to find capacitor values and other information by searching "Steinmetz connection."

• Hi and thank you for a detailed explanation. I will be using the multi tool machine for hobby purposes only. So i wont really want to invest to much money, and i can see a variable frequency drive can be a bit expensive. I updated my post with the picture of the wirings from the motors to the switch – mounim Jan 19 '17 at 20:07
• I don't think the switch wiring detail adds anything to my assessment of the problem. Unless you can re-connect the motor for 220 volt operation, you will need a transformer to step the voltage up to 380 volts and capacitor rated for 380 volts. The reconnection must be done with wires that are not now coming out of the motor. I will try to post a sketch. – Charles Cowie Jan 19 '17 at 23:34
• Thanks, i understand ... one more banal question really. So cannot just use the end wires as shown on the picture to make the conversion ? i should open the whole motor. Because it is embeded inside the machine, it is quite difficult to get it out, and to get to the casing it self. it is mach easier to just manipulate the end wirings. – mounim Jan 20 '17 at 11:59
• You can not use the six wires from the motor to the switch. Most motors have a box or a small cover on the side or end. There the internal motor wire are connected to longer wires going to the switch. If that is opened, you may find two wires spliced to each wire going to the switch. If that is the case, you have what you need. Continued - – Charles Cowie Jan 20 '17 at 12:15
• If you change those connections you must be very careful not to lose track of which wire is connected to each external wire. If you find only six wires, then the motor must be completely opened up. Finding the internal connections, disconnecting them and connecting them to 12 external wires is likely to be very difficult. The wires are solid rather than stranded. They are somewhat fragile. There is very little length to spare. They are soldered or welded. Special high-temperature insulating tape is used to insulate the connections. I have practically no experience with that. – Charles Cowie Jan 20 '17 at 12:22

A simple answer: 3 phase motors have 3 power connections (one can ignore U2, V2, W2). Connect mains L&N to 2 of those, and a capacitor from the 3rd to L or N. Your motor now runs.

The extra motor tappings & switches complicate the picture to add features.

• Thanks for the answer, but i am really not sure what capacitor should i use, should i use one according to the 0,37 or for the 0,51 Kw, and is a single capacitor is enough or do i need a starting capacitor as well ?. i am also confused about the wiring at the switch how to connect my capacitor to that . i just updated my question with a photo pf the switch – mounim Jan 19 '17 at 20:08

"The label on the motor shows : Volts : 380/380 KW : 0,37/0,51 U/min : 1430/2860"

A little confusion here, so let's put this in columns:

• Volts: 380/380
• KW: 0,37/0,51
• U/min: 1430/2860

In plain English:

• It's a 380 volt two-speed motor.
• At 1430 RPM, it draws 0.37 kW at full load
• At 2860 RPM, it draws 0.51 kW at full load

So now that we understand it's not a 380 kW motor, we can better solve this. :-)

If you have single phase 220 volts, there are phase converters (Google is your friend) to convert to 220 three phase. Then , you could use either:

• A 220 to 380v 3 phase .5 kva step-up transformer
• Three single-phase transformers wired as a 3 phase.

You may find the latter arrangement to be less expensive than a 3 phase transformer.

• The motor does not "draw" any kW. It could be said to draw X current under some stated load conditions. According to international standards (IEC and NEMA), power ratings listed on motor labels are the rated mechanical output. Input power is not listed, only the rated current and power factor. – Charles Cowie Jan 19 '17 at 22:04
• @Charles Cowie - I assumed that, but I edited it with your clarification. Thanks. – Mike Waters Jan 19 '17 at 22:20
• Technically, it does not draw 0.37 kW at full load, it produces .37 kW of mechanical power at full load and "draws" 0.37 kW plus losses. – Charles Cowie Jan 19 '17 at 22:42
• thanks guys .. very advanced discussion for me. transformers seems like an expensive solution. i guess i would just keep it with the capacitor solution. – mounim Jan 20 '17 at 0:03
• @Mike .. when talking about "220 to 380v 3 phase .5 kva step-up transformer" .. is this model suitable ? galco.com/buy/ABB/ACS143-1K6-3-U – mounim Jan 20 '17 at 12:32