# Designing a AC Snubber circuit for 2 hp using AC snubber

I am trying to control my 2 hp 240AC single phase motor with help of an arduino. Right now it is controlled via a contactor with 220-240 AC coil input voltage with help of NO and NC switches.

Following is what i am trying to achieve: Pardon my poor skills

Following is the 10A relay i am planning to use to control the contractor:

Following is the snubber circuit I have come to accept to the best of my abilities.

In the snubber circuit I am using 2000V 104J capacitor: Following is the image:

From what i could gather I am planning to use 20D271K as the varistor. Following one Varistor

My question is will this work? I apologise for poor circuit diagrams. I will get an electrician to install these. The motor will be switched on 2 times a day for roughly 30 mins.

Help is highly appreciated.

• Why the snubber? – winny Sep 17 '19 at 16:59
• From what i understood, motor being an inductive load, when switched on or off will produce a voltage proportional to the rate of change of current which could be very high. Same would also be experienced at the other end when the coil of contactor discharges. no? So to protect my 10A relay and arduino? – ANUNAY SINHA Sep 17 '19 at 17:04
• Are you using an SSR or a relay? – Voltage Spike Sep 17 '19 at 17:14
• XY problem. What is the motor or inductive current rating of the relay? – winny Sep 17 '19 at 17:16
• There is a contactor installed to control the motor: something like following: amazon.in/25Amps-4Pole-Contactor-240V-Catno/dp/B07N5LY8JG/… I am using the following relay: I dont seem to able to find the inductive current rating of the 10A relay. The installed contactor has been working fine using NO and NC switches for past 2 years. The 10A relay is: amazon.in/Generic-Channel-Relay-Module-Electronic/dp/B00C59NOHK/… Thank you for your help – ANUNAY SINHA Sep 17 '19 at 17:21

Don't switch the load directly! There is already a contactor in the circuit whose One Job is to switch the load. Have your relay switch the contactor coil.

Now you need a much smaller relay, and your snubbing problem is much smaller.

The contactor coil will also be an inductive load and may need snubbing, but nothing like the motor!

• That is exactly what I am trying to do. the snubber i have put is between the coil of contactor and the relay which is connected to arduino. I dont have experience in this field that is why I am asking if the circuit that i have drawn above using the resistor (100 ohms), capacitor (0.1uF) and the said veristor is fine or am i making a mistake? one thing i am getting is the issue wont be as pronounced as between the contactor and motor so maybe i could use following snubber? contd.. – ANUNAY SINHA Sep 17 '19 at 19:02
• cond.. [snubber from banggood - readymade] (banggood.in/…) – ANUNAY SINHA Sep 17 '19 at 19:02
• Relays don't need snubber protection from each other, unless you're overloading the relay. I would be more concerned about snubbing the Arduino side of the small relay so you don't fry the Adruino's outputs. That'll be DC so an overrunning diode would be fine. – Harper - Reinstate Monica Sep 17 '19 at 19:13
• Okay thank you for clearing that up. I have two questions 1. These relays have optical isolation. So if i separately power the relay using a separate 5V source (that is by removing the JD-VCC and VCC jumper), would that work? 2. Since these relays wont be dealing with high current, could i replace them with a solid state relay? contd... sorry for commenting like this – ANUNAY SINHA Sep 17 '19 at 19:27
• contd... 2A 240VAC Solid State Relay – ANUNAY SINHA Sep 17 '19 at 19:28

You can’t avoid the EMI of turn on/OFF using a ZVS controlled Triac.

E.g.

https://www.omega.com/en-us/control-and-monitoring-devices/relays/solid-state-relays/p/SSRL240-660

• Yes that is an option. But I was hoping to make use of existing components. crydom ssr are my back up. But they cost close to $100 when i convert from INR (Indian Rupee) – ANUNAY SINHA Sep 17 '19 at 19:08 • This Omega SSR is only$28. But you probably also want a snubber on the contactor contacts to extend their life. Consult Omron for details – Tony Stewart Sunnyskyguy EE75 Sep 17 '19 at 20:36