# How to connect 15kΩ NTC thermistor sensor to thermostat which requires 10kΩ NTC thermistor

I have a electric floor heating in my house. Old DEVI thermostat broke down few day ago. Problem is that DEVI thermostats are expensive and a little bit dump (not smart). I want to replace thermostat to with new one with smart functions. But every other model requires 10kΩ NTC. So i thinking what if i add 30kΩ resistor parallel to 15kΩ NTC thermistor = 10kΩ. The thermistor is firmly built into the wall, so it cannot be pulled out.

Temperature interval is about 15 °C to 35 °C.
Can anyone judge me this solution, please?

• That will work well at 25 C, ie when NTC resistance is 15k, but think about what happens when NTC resistance is 5k for example. The parallel resistance will be 4k3, which will introduce some error. Can you post specifics about the circuit? What is the NTC resistance at 15C and 35C? There will be errors with the solution you proposed, but maybe it is not significant. Commented Oct 14, 2020 at 19:38

If you want to shift resistance of NTC thermistor, you should do it with another NTC thermistor tied to the same object first thermistor measuring temperature of. If it can't be done, then you need to change biasing resistor in the thermistor's voltage divider circuit of your new thermostat. It is not ideal too, because you can't do anything with expected thermistor resistance curve, but your range is limited enough so it shouldn't contribute much to the error.

Example of why it is bad idea to shunt or offset thermistors (any kind) with fixed resistor:

10kΩ B3500 thermistor:
15C - 15029Ω
25C - 10000Ω
35C -  6832Ω

15kΩ B3500 thermistor:
15C - 22543Ω
25C - 15000Ω
35C - 10248Ω

15kΩ B3500 thermistor + 30kΩ shunt:
0C  - 17825Ω: measured as 11 °C
15C - 12871Ω: measured as 20 °C
25C - 10000Ω: measured as 25 °C
35C -  7638Ω: measured as 32 °C
50C -  5033Ω: measured as 44 °C


As you can see, the offset is pretty large, increasing faster with lower temperature. But if you swap biasing resistor in your new thermostat with correct one, overall error should be in range of 0.5-1 °C max. The correct new value of biasing resistor is 1.5x (15k/10k) if it's connected to VCC or 2/3 if it's connected to GND.

It's probably will be tiny SMD (0402) component in a dense environment, SMD rework station and some aluminum tape can be handy.