# Chaining multi-socket extention cords, can it be done safely?

I've always read that extention cords should not be chained. Also one should not build a tree of multi-socket cords. My background is physics, and I cannot see a problem with it, as long as one keeps in mind the current that flows. I might be neglecting something, that's why I want to make sure that I did not miss anything.

In Germany the electrical power is at 230 V, and fuses have current ratings of 10 A or 16 A. On many power strips I've seen that they have a maximum rating of 3500 W. The cable of the extension cord should be specified in a way that it can stand the current of around 16 A.

When using multiple extension cords, there are two fallacies that I can see:

1. People just see more sockets and connect more and more devices, going over the 3500 W of allowed current. The fuse might not trigger, but the cable will become hot and unsafe. This is something that I can easily avoid as in my use case would only have two nightstand lights and a phone charger at 100 W maximum.

2. The resistance of the total construction becomes so large that it will become a problem. Especially the DIN VDE 0100-600 seems to say that the resistance of the protective conductor must not be over 0.3 Ω for a cord up to 5 m length. For every additional 7.5 m of length, the resistance may go up by 0.1 Ω. The maximum may be 1 Ω. Assuming that individual cords are according to standard, I could hook up three of them; but that would totally ignore the resistance of the plug-socket-connection.

Where does the problem really come in? Is it that the protective conductor becomes useless if its effective resistance is too large? Or can I indeed chain power strips as long as I keep the total power consumption of that system well below the 3500 W threshold?

• What you state is correct and chaining sockets can be safe as long as all connections are good/solid connections with little contact resistance. However as more and more outlets are chained, more connections are needed so the chance that one (or more) aren't of good enough quality increases. That bad quality connection could make a bad connection and cause sparks and overheating. Most people cannot tell if a connection / connector is good enough so it is safer to keep the number of contact points small. Nov 15, 2020 at 14:16
• Consider that extension wiring introduces other hazards: crushing, chewing by pets. Extensions are also very often snaked upon floors, where water hazards are high. Nov 15, 2020 at 15:24